ZIMBABWE ELECTRICITY TRANSMISSION & DISTRIBUTION COMPANY
A Subsidiary of ZESA Holdings
REQUEST FOR COMPETETIVE QUOTATIONS (RFQs)
Tenders are invited from registered and reputable Suppliers / Companies for the supply and delivery of the following to ZETDC Northern Region.
|RFQ NUMBER||DESCRIPTION OF REQUEST FOR QUOTATION(RFQ)||CLOSSING DATE|
|RFQ 120 /2017||Supply and delivery of-;|
8 x 12v 100 AH solar or deep cycle batteries
*NB please refer to the attached specifications.18/12/2017
@ 14.00 hrs
Quotations must be enclosed in sealed envelopes and clearly endorsed on the outside with the advertised RFQ number, the description of the Request for Quotation (Purchase), the closing date and must be posted in time to be sorted into Post Office Box No. 293 Chinhoyi or delivered by hand to the Tender Box ZETDC Northern Region Stand Number 5310 North Drive Chinhoyi on or before 14:00hours on 18 December 2017.
Tenders should be accompanied with the following documents;
- Delivery period should not be more than 7 (seven) working days
- Vat registration Certificate / Current Tax Clearance Certificate (I.T. F263)
- Prices should be in USD dollars.
Late bids will not be considered.
Tenderers are free to witness the opening of tenders on the closing date and time.
ZETDC does not bind itself to accept the lowest or any tender and reserves the right to accept the whole or part of any tender.
For further details, please contact The Procurement Office on telephone numbers 067-23784/25735-9 /23071-3 /0772 332 214/0716 957 230/0772 425 825
GENERAL MANAGER (NORTHERN)
ZETDC NORTHERN REGION
DEEP CYCLE BATTERY SPECIFICATION
|1||Battery Bank Voltage||48V DC ( Bank of 12V batteries or specify offer)|
|2||Nominal Minimum Capacity||96Ah|
|3||Standards||IEC 61427 or IS13369 or equivalent|
|5||Type||Prefer SMF (Sealed Maintenance Free)|
a) The battery shall have a life expectancy, not less than 10 years when operated at 25 0C and under float conditions.
b) The batteries shall be tested to IEC 68-2-29, test certificate to be included with the bid.
c) The battery shall not accumulate salts on the terminals during its operation.
d) The battery shall be hermetically sealed to avoid the ingress of moisture and insects.
e) Nominal voltage per battery should be specified.
f) The batteries should come with battery rack and fully insulated connecting cables.
g) The manufacturer of the batteries shall have ISO 9001 or 9002 Certification, which shall be included in the bid. Test Reports shall also be submitted with the bid.
- Rated voltage: As per schedule of requirements
- Capacity minimum: Capacity per battery should not be less than 96Ah.