Client Service Centre: Victoria Falls
(1)Pandamatenga 33 kv line date and time of fault occurrence :12/11/2017 17:25.
Number of customers affected 9 including export to Botswana BPC..
Found 1 x 12.6 mts vertical strain wood pole sharttered by lightning is being changed today.
(2)Airport feeder 11kv line reported @ 12:00hrs 13/11/2017.Found 1x 10.8mts wood pole struck by lightning.To be replaced tomorrow.
Number of 160 including Chisuma,Jambezi (Tel One,Econet & Telecel sites).
(3)Victoria Falls Aerodrome area 1 x 100kva 11/0.4kv transformer struck by lightning.Number of customers affected 15.Temporarily installed 1 x 200 kva transformer
Meant for Aerodrome S/Stn V1a008.